SMART WARM is certified and complies with the latest quality standards:
– EMC Test File No. C20060470
– EN55014-1:2000 + A1:2001 + A2:2002
– EN55014-2:1997 + A1:2001
– EN61000-3-2:2000, EN61000-3-3:1 995+A1:2001
In the unlikely event that your system does need a repair, we are able to provide fast and efficient support. We will ensure that it is back to its usual highly quality service in no time, giving you peace of mind that it is fully functioning and reliable.
PRODUCT DESCRIPTION AND TECHNICAL SPECIFICATION
The product consists of the power supply, the heat exchanger, and regulator (thermostat).
The power supply is delivered in a steel housing, protected against corrosion and the usual physical loads. It is usually installed under the plaster, close to the electrical cabinet. The only thing visible is the cover.
The heat exchanger consists of aluminium strips, 6, 8, 12, or 17 cm wide, and 0.2 mm thick. They are installed under or on top of screed in the floor, or under plaster panels or plaster in the walls, and powered with a low-voltage electricity (from 3 V to 48 V).
Heating strips can be installed on top of existing flooring.
The power supply capacity is determined by the heat loss of the room that is heated.
Heating strip dimensions depend on the desired specific heat output (W/m2) of heating and energy rate of the building.
Specific heat output is limited by the recommended floor temperature in individual rooms. Specifically:
23–28°C for living areas (specific heat output 30–80 W/m2)
28–32°C for bathrooms or margins along external walls or under glass surfaces (specific heat output 120 W/m2)
For heating open areas or surfaces (terraces, balconies, driveways), we use a heat output of 80–150 W/m2
If heat loss of closes areas required a higher specific output than recommended, we can supplement it with wall installation or by redirecting into passive floor surfaces.
SMART WARM TECHNICAL DATA
Heat exchanger: Insulated Al strips
Power supply: 3–48 V (optional connection to alternative energy sources)
Specific power: By calculation or optional
Floor temperature: 23–28°C, bathrooms 32°C (or optional)
System power supply: 220–230 V, 50–60 Hz
Maximum power consumption: 12 A
Regulation: by room, stationary or remote
Protection: OF, F1 + F2, soft-start
Heat exchanger protection: Chemical, physical
Warranty period: 20 years for heating strips, 5 years for electronic circuitry
Flooring: All types
Installation: Floor, wall, or combined
Screed: Wet or dry
Issued by: SIQ, Slovenian Institute of Quality and Metrology
Tržaška cesta 2, SI–1000 Ljubljana